Scope of work was to provide Full MEP Design and Engineering for a Miracle Math TI (1,400 SF) at location
MEP Design and Title 24 for 5,900 SF SD Home Buyer Office TI in San Diego
InnoDez provided MEP Design and Title 24 Report for San Diego Home Buyer office tenant improvement.
Location: 7580 Trade St. San Diego, CA 92121
Size: 5,900 SF
Two Rooftop units with an economizer have been installed at roof, Ventilation rate has been calculated based on the CMC 2019 Table 402.1. Supply ducts were provided at ceiling with a maximum duct size of 16 inches.
All bathrooms have been provided with an exhaust fan with louver at roof.
HAP has been performed to calculate the cooling and heating loads, equipment has been selected based on Carrier Datasheet.
Water Supply has been provided based on Table 604.1 from the CPC to verify the size of the main pipe and the water meter size.
The rooftop units were gas heating and electric cooling, gas pipes were schedule 40, gas isometric has been done.
Lighting fixtures were selected based on the RCP provided by the client.
Three panels have been selected with a total power of 1200 A.